S-2.1, r. 4 - Safety Code for the construction industry
3.4.4. In addition to the standards prescribed in section 3.4.1, portable fire extinguishers shall:
(1) be of type ABC approved by Underwriters’ Laboratories of Canada (ULC);
(2) be loaded;
(3) comply with:
(a) NFPA Standard 10-1975 Portable Fire Extinguishers, where the extinguishers are manufactured before 1 January 1989; or
(b) NFPA Standard 10-1988 Portable Fire Extinguishers, where the extinguishers are manufactured on or after 1 January 1989;
(4) bear the name of the person responsible for their maintenance and indicate the date of the most recent inspection;
(5) be easily accessible.
R.R.Q., 1981, c. S-2.1, r. 6, s. 3.4.4; O.C. 329-94, s. 32.