213. Every fill pipe on a tank for storing motor fuel, except fill pipes on a tank connected to a generator engine using diesel fuel or diesel fuel containing biodiesel, must extend to a distance of not more than 200 mm from the bottom of the tank.
O.C. 221-2007, s. 1; O.C. 88-2018, s. 241.