115. The owner of a petroleum equipment installation that includes at least one component that is high-risk petroleum equipment must provide the Board at the following inspection intervals with a certificate of conformity of the equipment that meets the requirements of section 117, produced and signed by a recognized person: (1) for underground petroleum equipment
(a) having a double wall without an automatic leak detection system or having a single wall, every 2 years; or
(b) for fuel oil or having a double wall with an automatic leak detection system, every 4 years;
(2) for bulk plants, every 2 years; and
(3) for aboveground petroleum equipment, every 6 years.
If a private inspection program referred to in Division V of Chapter III of the Act respecting petroleum products and equipment (chapter P-29.1) as it read on 31 March 2007 ends and at least 6 months remain before the expiry of the permit, the holder of the permit must provide the Board with a certificate of conformity before that date.